Can check and control all indoor units through built-in Web server functions.
Can directly connect with indoor/outdoor units without centralized controller CCM30/CCM03 and monitor controller CCM02.
Can control indoor units, configure gateway through Web function in the LAN.
Can connect to the BMS system through TCP/IP or RTU.
BMS system can control and get the running real-time data of the air conditioner through CCM-18A.
CCM-18A/N-U can be connected up to 16 indoor unit
When the baud rate of the outdoor unit is 600, can be connected up to 64 indoor units and 4 outdoor units.
4 outdoor units must be in the same system and the indoor units can be from different systems but address is not repeated.
WAN port: Connect to the router by 5 Ethernet cables to ensure that PC can access to the web page.
A1B1E port: Connect to the XYE ports of the indoor unit and the K1K2E ports of the outdoor unit
A2B2E port: Connect to the terminal serial port.
POWER port: Offer DC 5V
Reset button: Can reset to the original setting.
Can control the unit and configuration the gateway through WEB function in the LAN
Can be connected to the BMS system through TCP/IP or RTU mode
One Modbus gateway can bridge one refrigerant system with a PC or the Modbus master
The PC system with the Modbus protocol port can communicate with CCM-18A through RTU or TCP/IP
method to control and monitor units. There are two methods for your reference.
1. If it doesn’t monitor the ODU’s states, it can directly connect to the XYE ports of the indoor/outdoor units in both ways above.
If it connects to XYE ports of master ODU, ODU must be set to auto addressing mode.
XYE and K1K2E must be connected hand by hand.
It supports two kinds of baud rates (600 and 4800) of the outdoor unit can be connected. Baud rate is 600: V4 Plus and D4 plus series; and baud rate is 4800: V4 and D3 series.
One Modbus gateway can bridge one refrigerant system with a PC or the BMS system (Modbus master).
When the baud rate of the outdoor unit is 600, can be connected up to 64 indoor units and 4 outdoor
When the baud rate of the outdoor unit is 4800, can be connected up to 60 indoor units (indoor address
must be from 4 to 63) and 4 outdoor units.
The addresses of accessed indoor/outdoor units can’t repeat; 4 outdoor units must be in the same